Architectural eight inch horizontal down light rated for use with two quad or triple tube lamps. For use in existing sheet rock ceilings where access is only available from below the ceiling. Use in non insulated ceiling, where insulation can be kept 3" from fixture, and 1/2" from adjacent building components. Adheres to the minimum lumens to watts ratio that qualifies to Energy Star.
Ballast Type: 26W 120V Electronic
Lamp Types: 2 x 13W 4-Pin Quad or Triple (not included)
Dimming Options: Variety of Electronic Dimming ballast options are available in 13W. Please match appropriate fixture with compatible compact fluorescent dimming control.
Emergency Option: 90 minute battery back-up must be ordered and installed as a self contained kit set apart from the frame-in.
Fuse Option: 2A Fuse may be added to any compact fluorescent frame-in. Add suffix FS.
Minimum Clearances: Non-IC housings require a minimum clearance of 3" from thermal insulation and 1/2" from adjacent building components
Installation: High tension tempered steel springs secure remodel housing evenly to ceiling; hole cutout template provided for convenience.
Plaster Frame: Architectural quality 0.050 galvanized steel ring riveted to elevated 0.064 steel junction box and ballast tray.
Socket Cup: Die-cast formed galvanized steel with two 4-pin sockets. The socket cup attaches to the finishing trim with two present screws that allow for minor rotation within two keyhole slots and a third fixed position anchor screw.
Width: 8 1/2"
Depth: 7 1/2"
Ceiling Opening: 8 1/4"
If in stock, item ships in 3 to 5 business days.
cULus Damp Location with Feed Through
cULus Wet Location (Only with designated trims)
Energy Star qualified
This product hasn't received any reviews yet. Be the first to review this product!